Table of Contents

## Why is cable sizing calculation important?

To ensure safe operation and work on full load without being damaged cable sizing calculation is very important. It helps us to provide suitable voltage for the load.

Besides this proper sizing help us to withstand the worst short circuit current, and ensure device safety during operation.

In this article, we will discuss methodologies and other related parameters regarding cable sizing calculation. **And of curse we will give a simple example to choose a cable. **

**Cable Sizing Calculation Steps**

The process of the size calculation method consists of six steps.

- In the very first step, we collect data about cable, load, and environmental conditions.
- The second step is to determine the minimum cable size for continuous current carrying capacity.
- The next step is to determine the minimum size of the cable based on voltage drop.
- Determine the minimum size of cable for short circuit conditions.
- The fifth step includes determining the minimum size of the cable in case of earth fault loop impedance.
- The final step is to select the minimum size of cable in the previous steps.

I have created an android app to help you in selecting cables, The app is 100% FREE, it has the most common cables tables. Such as current ampacity tables, short circuit tables, derating factors tables and more. These tables are simple in design to make it easy for you to use it. I will be happy if you install the app from here.

electrical4uonline

Now we will discuss each step in detail to find the correct size of the cable.

## Example of cable sizing step by step

Assume we have:

- power of load, P = 80KW
- The load is at 200 meters distance of source
- Three phase, V = 415V
- power factor is, pf = 0.8
- 5% allowable voltage drop
- direct buried in ground
- 1 meter burial depth
- 35 °C Ground temperature
- one cable per trench

**Ok, let’s choose the cable step by step**

Load **current I** = (Power in watt) / (1.732 · V · pf )

= (80· 1000) / (1.732 · 415· 0.8)

= **139 A**

**Determine*** correction factors*

*correction factors*

From derating factor tables we find the derating factors of the example conditions.

For more details about derating factors read our article **What is derating factors of underground cables?**

- correction factor of ground temperature =
**0.89** - correction factor of soil =
**1.05** - correction factor of cable burial depth =
**1.0**

* Total derating factor = 0.89 * 1.05 * 1.0 *=

**0.93**

From cables ampacity tables. Selecting** Copper, XLPE**, **3*50+25 mm ^{2 }**, its current is

**185 A**, Derating this current

**185 * 0.93 = 172 A**

**Calculating voltage drop** of this cable, VD = 0.715 MV/A/M, from voltage drop tables.

VD = 0.715 * distance*load current = (0.715/1000)*200*139 =19.877 V

**The allowable voltage drop = 415 * 5% = 20.75V**.

**This means that the cable is accepted because the voltage drop is in limits (5% = 20.75 V)**

Finally, we can use a cable of **Copper, XLPE**, **3*50+25 mm ^{2}** for the load and laying conditions mentioned above.

### Important notes:

- In this example we skipped short circuit calculations, as it’s much complicated and depend on many factors.
- Voltage drop and The current carrying ampacity of the cable which are
**0.715 MV/A/M**, and 185A, are on my android app “CABLES TABLES“. I made it my self.

**Conclusion **

- Choosing power cable of electrical loads depend on load current, cable ampacity, installation conditions etc.
- Cables currents tables are in “CABLES TABLES” android app.
- Derating factors should be applied to the cable current.
- Voltage drop value should be in the accepted limits.
- If the cable voltage drop is higher than the limits, then we choose the larger sized cable.

## Best FREE Electrical Apps

**I was a fresh graduate, from the electrical engineering faculty, **when I realized that I needed many electrical formulas, tables, and calculations in my work.

I never like memorizing this stuff and carrying cable catalogs every where.

**So I created my own simple custom android apps to help myself. It feels great that I have my solution!**

Then, I published these apps, **100% FREE,** on the google play store, to help you at your work. **Install the apps, No Fees, No credit card needed.**

**Cables tables**cables most used tables, I use this one all the time.**Fast Electrical Calculator App**, the one I use for electrical calculations, I always count on this baby the most.**Motor Calculator App**is a simple app for electrical motor calculations.**Cables Ampacity Tables App**we need cable ampacity almost every day, in this app, I made it easy for you to check cable ampacity.**Circuit breaker Selection App**This one is a fast way to determine circuit breaker sizing.

**I will be happy if you use one of them, share it, and rate it on the market.** This way you help me continue updating the apps.